REPLACE THE SEPTIC TANK. HERE IS A PUMP SYSTEM WHICH CALLED FOR A 1250 GALLON TANK. WE UNGRADED TO 1530 GALLONS, FREE OF CHARGE. WE INSTALLED A 500 GALLON PUMP TANK WITH A .75 HP PUMP. FOR THE FIELD, WE TRENCH 32 LINES BY 100′ USING 4 VALVES.
Design of system: Homestake Soild Testing and Drilling
Aggregate Supplier: NA
Plastic Supplier: Plastics Inc.
Tank Supplier: Plastics Inc.
This customer needed a new tank and field. We started with pumping, then destroying the old tank.
More digging of old tank; from the 1950’s we believe.
We had to trench an electrical line for the pump and alarm float. This trench unfortunately went through the client’s front yard to the breaker box. =(
100′ trench to the field.
32 trenched lines 100′. 4 Values systems. Sniffer valve at high point.
Another successful installation from: