HERE IS A CONVENTIONAL GRAVITY SYSTEM FOR A DOG KENNEL WHICH CALLED FOR 2500 GALLONS WORTH OF TANK. WE UNGRADED TO 2 1530 GALLONS. WE INSTALLED 138 INFILTRATOR CHAMBERS IN 6 3′ BY 100′ TRENCHES AND INSTALLED A DISTRIBUTION BOX WITH FLOW EQUALIZERS.
Design of system: W.W. Enterprises
Aggregate Supplier: NA
Plastic Supplier: Plastics Inc.
Tank Supplier: Plastics Inc.
County: Arapahoe (Tri County)
We installed the two tanks in series with 12″ to 18″ risers.
Tri County requires a sweeping T for your inlet T. Don forget that!
About 70′ trench down to the field. 5% slope.
Excavation to spec. 3 foot wide trenches, 100′ long, and 6′ between each trench.
Passed inspections. Time to backfill!
Another successful OWTS system installed by TBC. Contact us today for a quote.